In the event of a power outage or disconnection from the shore or the generator, the Multi's converter activates automatically and takes over the supply of the connected loads. This transfer is so rapid (less than 20 milliseconds) that the functioning of computers or other electronic equipment will not be disturbed.
The complete bridge topology with a toroidal transformer has proven its reliability for years. The converter is protected against short circuits and overheating, whether in the event of overload or high ambient temperature.
Strong starting power
Necessary to start loads with a high inrush current such as power converters for LED bulbs, halogens or power tools.
PowerControl - Adapt to the limits of a generator, dock or sector (800 VA / 1200 VA)
The Multi Control control panel makes it possible to limit the power to be supplied by the quay or by the generator. The MultiPlus then takes into account the power demand of other AC loads at the output and will only use the excess for the load, thus avoiding any overload of the shore or generator supply.
PowerAssist - More power supplied by the quay or the generator (800 VA / 1200 VA)
In case of peak power demand - often required for a short time - the MultiPlus will ensure that insufficient generator or shore power is compensated by additional power from the battery. And when demand decreases, the excess power will be used to recharge the batteries.
If the Search mode is in the "on" position, the power consumption of the converter is reduced by around 70% if no load is available. Thanks to this mode, when the Multi operates in converter mode, it is stopped in the event of no load or very low load, then switched on every two seconds for a short period. If the load current exceeds the set level, the converter continues to operate. Otherwise, the converter stops again.
By default, the programmable relay is configured as an alarm relay, i.e. the relay is deactivated in the event of an alarm or pre-alarm (converter almost too hot, input ripple almost too high, battery voltage almost too low).
Remote On / Off / Charger On Three-pole connector.
Remote monitoring and control
Supervise and control your MultiPlus and the system or systems locally (LAN) or remotely over the Internet, from anywhere in the world, using the free VRM portal website and the free VRM app. You can access it from a phone, tablet, laptop or PC with different operating systems. Thanks to the required Color Control GX or Venus GX, there is no limit in terms of control: whether to adjust your MultiPlus or to configure a geo-location for rented vehicles, and much more ...